You are watching: What gauge wire for 60 amp service
6AWG copper wire would certainly be the minimum because that a 60A subpanel however with a 105ft distance you have too lot voltage drop and need to go as much as 4AWG copper to save the voltage drop within acceptable boundaries (usually 5%).
The National electric Code publication / write-up 110.14 (c)(1) identifies temperature limitations for circuits and feeders of 100 amp or less. If the circuit is 100 amp or much less you have to size the conductors based upon the 60-degree celsius pillar unless the breaker and also the devices terminations space rated for 75 or 90 degrees.
You need to use a #4 conductor to feeding a 60 amp circuit.
Thanks for contributing response to Home improvement Stack Exchange!Please be certain to answer the question. Carry out details and also share her research!
But avoid …Asking for help, clarification, or responding to other answers.Making statements based on opinion; ago them increase with referrals or an individual experience.
See more: How To Get Angie'S Pink Slip In Need For Speed Carbon Pink Slips ?
To learn more, check out our advice on writing good answers.
write-up Your prize Discard
Not the price you're spring for? Browse various other questions tagged electrical subpanel or questioning your very own question.
What size wire essential for 100a subpanel 120ft away from house sub panel? greatest amp draw will it is in a window A/C unit, and a swimming pool pump
site style / logo © 2021 ridge Exchange Inc; user contributions licensed under cc by-sa. Rev2021.9.24.40305